500-kV XLPE Underground Cable Line Construction for Sustainainability Electric Power Transmission in City Centers
Keywords:Keywords: Overhead line, Underground cable, Cable, 500 kV, Transmission, Investment cost, Construction Cost, Ratio.
Abstract. 500-kV Underground Cable transmission line design is a type of design that has never been applied in transmission line construction in Indonesia. Even around the world, 500 kV Underground Cable designs are still limited scale. Actually, electric power transmission line grid systems in Indonesia with a voltage rating 500 kV has been applied, but only in Java island with Overhead Line transmission line model, and it’s a backbone of the Java-Bali power grid system. Currently, PLN have a Jakarta Looping transmission system project 500 kV Extra High Voltage. This project has a potential delays due to land problems and social constraints along the route. Given that Jakarta is a capital city with a very high population, the construction of a tower transmission line will be a special challenge to complete the transmission project, where the process of land acquisition and compensation costs under along the route (ROW) will also be a special thing. In this research, we will try to estimate the construction cost for the 500 kV Underground Cable as an alternative to the project for other types of aerial cables. The route length will be adjusted into 4 categories of the overhead line route 1)a half of the overhead line route, 2)same with the overhead line, 3) 1.5 times of overhead line, and last 4) 2 times of overhead line. From the estimated calculations with these 4 categories, it is obtained the ratio of construction costs with underground cable designs to the overhead line design is smaller than cost of ratio for the same project design in Europe and/or America. It’s feasible to execute in urban area like Jakarta, Surabaya and Bandung, but not feasible for outside urban area.
Ichimaru, Shota. 2019. Route design and cost estimation for JapanRusia and Japan South Korea Interconnections. Global Energy Interconnection. Tokyo-Japan. Kabel Metal Indonesia. www.kmi.co.id Larsen, Peter H. 2016. A Methode to estimate the cost and benefits of undergrounding electricity transmission and distribution lines. Ernest Orlando LawrenceBerkeley National Laboratory. LS EHV Cable System. 66-500 kv XLPE Cable and Accessories, 2008. www.lscable.com Mahmudi, Amin. Deternination of the Ampacity of Burried Cable in Non-Homogenous Environmental Condition by 3D Computation. Dept. of Electrical Engineering Univ. Technology. Iran Mcllwraith, John. 1996. Underground Power Cable : Cost and Benefits. Science, Technology, Environment and Resources Group. Moutassem, Wael. 2010. Configuration Optimization of Underground Cables Inside a Large Magnetic Steel Casing for Best Ampacity. Departement of Electrical and Computer Engineering, University of Toronto. Nurhadi, Irfan. Analisis PD Pada Saluran Kabel Tegangan Menengah 20 kV (Studi Assesment SKTM di PT. PLN (Persero) UP3 Menteng). Univesitas Negeri Jakarta. Naderin, Ali. 2017. Comparison of High Voltage Cables with Existing Overhead Lines to Increase Energy Security in the Westfjors of Iceland. Metsco. Natinoal Grid. 2015. Undergrounding High Voltage Electricity Transmission Lines, the Technical Issue. www.nationalgrid.com Peraturan Menteri ESDM No. 27 Tahun 2018. Kompensasi atas tanah,
bangunan dan atau tanaman yang berada di bawah ruang bebas jaringan transmisi tenaga listrik. Menteri ESDM. Indonesia. Public Service Commision of Wisconsin. 2011. Underground Electric Transmission Line. USA. www.psc.wi.gov Ritter, Fred. 500 Kv ac Underground Transmission Evaluation, Technical Lead – Engineering, Alberta Electric System Operator. SPLN T5.006. 2019. Ruang bebas dan jarak bebas minimum pada saluran udara tegangan tinggi (SUTT), saluran udara tegangan extra tinggi (SUTET) dan saluran udara tegangan arus searah (SUTTAS). PLN Puslitbang. Suzuki, Akira. 2000. Installation of the World’s First 500 Kv XLPE Cable With Intermediate Joints. Furukawa Review. Tokyo Electric Power Co.Inc Umeda, Shinji. 2007. Underground Power Cable. Distribution Cable, Overhead Transmission Line, Industrial Cable and Their Accessories. Furukawa Electric Industrial Cable. Voksel Electric. www.voksel.co.id Pfisterer, www.pfisterer.com Wendt, Volker. 2017. Undeground Cables in Europe. The European Association of Wire and Cable Manufactures and National Association. Eurapacable. Working Group, Statistic of AC Underground Cables in Power Network. ISBN 978-2-8573-026-1 WSP. 2018. Assesment of Technical Alternative to Strengthten The 400 Kv Transmission Grid. Independent Report. Newcastle. Xynis, P and I. Papagiannopoulos. Optimal Position of Burried Power Cables. Elektronika Ir Electrotecnika. Gent University. Belgium.